Question about Goodman GMS90703BXA Heater
Installed furnace with two zones, main floor with stat with 24 volt acuator/baffel in air supply and bed room down stairs with stat with 24 volt acuator/baffel in air supply. how do i wire the stats to control the heat and air cond. and also control the acuators
You will need a control to operate motorized zone dampers. In the ductwork, you will install a damper in each line going into the area you want zoned. If you have air conditioning you will also require a barometric relief damper that allows air to pass thru the ductwork and not restrict air over your A/C coil. Common controls are made by Honeywell and EWC.
If you already have the control module, you will run two or three (low voltage) wires from each motorized damper back to the control. Your thermostat wires (also low voltage) will run from each thermostat to the control module and connect to a zone relay. Match each zone by number. You will need to run power to the control module that will provide power to the thermostats as well as the motorized damper. Check on the reverse side of the control module and/or check on the web to find the wiring diagram.
Posted on Nov 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2017 | Heating & Cooling
Jan 09, 2017 | Coleman Heating & Cooling
Jan 08, 2017 | Coleman Heating & Cooling
Jan 07, 2017 | Heating & Cooling
Jan 03, 2017 | Royal Heating & Cooling
Jan 02, 2017 | Heating & Cooling
Dec 28, 2016 | Heating & Cooling
Jan 03, 2015 | Heating & Cooling
Nov 11, 2014 | Heating & Cooling
Aug 12, 2014 | Heating & Cooling
147 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: