Question about Heat Controller Thru-Wall/Window Air Conditioner
I have a trane thur wall unit in one of my rentals. It is a year old and was removed from a hilton hotel. I had it put in its nice and level so I think. I had an electrition put a new plug on the end of it and new wall plug to match it up. Heater call for 20 amp and we have a 20 amp breaker. The 220 was already there for air conditioner. Electrition check it is drawing what it should. The unit when turned on will come on you can feel heat coming out just a bit, and thats on high. The fan does not come on when on heat mode. When turned to cold air unit kicks on harder then it does on heat, and the fan starts to turn. The air does blow and works. I'm not sure if it is working as it should though it does blow harder then when it is on heat. Please if you have any suggestions please let me know. Thanks Tim
The fan for the A/C should blow harder than in heat. The fan should be on high for cool and low for heat. You can change the heat setting for medium but I would not recommend it because it may make heat coming out feel less.
Posted on Feb 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 21, 2015 | Heating & Cooling
Jan 04, 2013 | Heating & Cooling
Jan 24, 2011 | Heating & Cooling
Jan 10, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 02, 2010 | Heating & Cooling
Oct 20, 2009 | Amana PTH123B25AJ Heat Pump Air...
Jul 27, 2009 | Heating & Cooling
Mar 20, 2009 | Heating & Cooling
Jan 21, 2009 | Heating & Cooling
155 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: