Question about Goodman GDS80904BNA Open Flame Heater
The blower on exaust will stay on and wont shut off the light blinks 4 times it says open limit switch
This information saved was incredibly useful and I appreciate the shared knowledge. Thanks much!
Posted on Jan 21, 2009
There is a Primary High Limit Switch towards the middle of the furnace, it more than likely needs to be replaced, very common to go out only after a few seasons. Also, you could have a flame rollout switch tripped that will signal the same code, these switches are re-settable and are located on the outer, top and sides of the burner assembly, they’re about ½ inch in diameter with a red push button in the center and two wires “ usually purple” coming off of them.
Hope this helps
Posted on Dec 02, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 04, 2016 | Goodman Heating & Cooling
Oct 12, 2011 | Goodman GMS90703BXA Heater
Oct 02, 2011 | Goodman Heating & Cooling
Sep 06, 2011 | Goodman Heating & Cooling
May 22, 2011 | Goodman Heating & Cooling
Apr 17, 2011 | Goodman Heating & Cooling
Dec 03, 2010 | Goodman GMS80903BNA Heater
Sep 12, 2009 | Goodman GMS90703BXA Heater
Apr 01, 2009 | Goodman Heating & Cooling
Jan 24, 2008 | Goodman GMS90703BXA Heater
591 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: