Question about Air Conditioners
Sounds like its not proofing flame. it has a sensor usually like a needle sticks out into the flame that tells the gas valve the flame lit and is burning so its ok to keep sending gas, if its fails to proof flame then burner shuts down, then it tries to relight 3 times then locks out on fail safe. the blower will sometimes run continually once that occurs to highlight a failed condition. every time you reset it will try again 3 times then shut down. lp gas is very dangerous, even i do not work on it as the gas acts like gasoline and lays around. not like natural gas that disperses well. if you see the flame sensor try gently cleaning it with a little emory cloth. also a loose ground can cause this. check tio be sure any green wires are snug , they actually flow volts to ground through the flame on some to proof, thats why no ground no flame. if that fails then the board is most likely problem. change wire for wire , or get generic replacemant and follow directions exactly. good luck.some ignitors act as a flamre proofer as soon as they are done igniting! rarely do they fail to perform both funtions.
Posted on Nov 21, 2008
Tips for a great answer:
Jan 07, 2011 | Air Conditioners
Nov 28, 2010 | Ruud UBHC Air Conditioner
Nov 19, 2010 | Air Conditioners
Jan 16, 2010 | Weather King Air Conditioners
Jan 11, 2010 | Bryant Air Conditioners
Jan 04, 2009 | Air Conditioners
Dec 13, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 28, 2008 | Air Conditioners
Nov 06, 2008 | Air Conditioners
Dec 01, 2007 | LG Heat cool Window Air Conditioner
215 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: