Question about Heating & Cooling
Sounds like its not proofing flame. it has a sensor usually like a needle sticks out into the flame that tells the gas valve the flame lit and is burning so its ok to keep sending gas, if its fails to proof flame then burner shuts down, then it tries to relight 3 times then locks out on fail safe. the blower will sometimes run continually once that occurs to highlight a failed condition. every time you reset it will try again 3 times then shut down. lp gas is very dangerous, even i do not work on it as the gas acts like gasoline and lays around. not like natural gas that disperses well. if you see the flame sensor try gently cleaning it with a little emory cloth. also a loose ground can cause this. check tio be sure any green wires are snug , they actually flow volts to ground through the flame on some to proof, thats why no ground no flame. if that fails then the board is most likely problem. change wire for wire , or get generic replacemant and follow directions exactly. good luck.some ignitors act as a flamre proofer as soon as they are done igniting! rarely do they fail to perform both funtions.
Posted on Nov 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 07, 2011 | Heating & Cooling
Nov 28, 2010 | Ruud UBHC Air Conditioner
Nov 19, 2010 | Heating & Cooling
Jan 16, 2010 | Weather King Heating & Cooling
Jan 11, 2010 | Bryant Heating & Cooling
Jan 04, 2009 | Heating & Cooling
Dec 13, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 28, 2008 | Heating & Cooling
Nov 06, 2008 | Heating & Cooling
Dec 01, 2007 | LG Heat cool Window Air Conditioner
215 people viewed this question
Usually answered in minutes!