Question about Heating & Cooling
My girlfreinds house is old and the furnace is a Royal Jet Flow FG-2-55 Gravity Vented natural gas fired furnace.
I cleaned the thermal coupler and flame sensor and the furnace now burns longer and works great! Except, now when it starts the gas flows for about 1 to 2 seconds before it ignites. This causes a good flash and about a 6-inch flame flashs out of the venting. Needless to say this is not good.
did I do something wrong, or do I need to adjust the pilot flame making it larger or do I need to replace something? I tried cleaning the burner but it only worked for about two firings then it started and got worse (3 or 4 seconds) before it ignited BOOM!
try cleaning the crossovers between the burners. Also look closely at the flame and make sure that the burner is firing all the way to the pilot. Sometimes its just a few little holes that vent a little gas to give the flame a path to follow will be stopped up and cause the condition you describe
Posted on Nov 18, 2008
The humming sound might be a stuck blower motor or a motor that won't start due to defective starting capacitor.
Posted on Nov 06, 2012
Tips for a great answer:
Jan 22, 2016 | Heating & Cooling
on Dec 07, 2009 | Heating & Cooling
Feb 10, 2011 | Heating & Cooling
Dec 07, 2009 | Weather King Heating & Cooling
Nov 12, 2009 | Heating & Cooling
Jan 29, 2009 | Goodman GDS80703ANA Open Flame Mid-Size...
Jan 26, 2009 | Heating & Cooling
Nov 18, 2008 | Williams 2509612 Ceramic Mid-Size Heater
Oct 07, 2008 | Heating & Cooling
970 people viewed this question
Usually answered in minutes!