Question about Procom ML300TBA Heater
Propane appliances usually run on 10-11 inches of water column, this is about 1/2 pound of pressure. If the regulator you have is not rated for delivering gas at that rate, you will need to find one that does. If your regulator is rated for more than the 11 inches, most likely you could have damaged the appliance regulator that came with the heater. Check the propane pressure specified by the heater manufacture against the rated supply of your regulator and see if they match. Make sure the heater is rated for Propane and NOT Natural Gas. Check to see if the gas valve on the appliance is in the operate position and all valves are open. Bleed off the air in the gas line by holding down the pilot switch and keep attempting to light the pilot. It could take you a few minutes. If you hear and smell gas but the unit will still not light, don't chance at getting hurt, call a technician. Look to make sure there are no safety switch that may have triggered off not allowing the gas valve to operate. And make sure there is no obstruction in the heater?s gas valve blocking off the supply of gas. Always exercise caution when it comes to gas and if you are uncomfortable, call a qualified gas technician.
Posted on Sep 17, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 03, 2016 | Procom Heating & Cooling
Dec 06, 2012 | Heating & Cooling
Dec 14, 2010 | Procom 10K BTU, Vent Free, 2 Plaque...
Dec 13, 2010 | Procom MN100HPA Heater
This heater is designed to work with LP gas. You will need a regulator from the tank to the heater set at 11"wc .that's standard for any LP gas system. Your existing piping system should have a regulator already outside of your house before the gas inters your home .If it does not then you will have to install one. The regulator can be inside but you will have to run a vent line in copper from the regulators vent to the outside of your house.
Hope this helps ......
Nov 23, 2010 | Heating & Cooling
Oct 28, 2010 | Heating & Cooling
Feb 26, 2010 | Procom ML300TBA Heater
Nov 06, 2008 | Heating & Cooling
Oct 26, 2008 | Procom ML300TBA Heater
584 people viewed this question
Usually answered in minutes!