Question about Reddy Heater RLP100 Portable Forced Air Propane Heater with Variable Heat Ouput
Model # r-15 wall propane heater..empire corcho
i get the pilot light to light but when i try to get 1 brick or 2 bricks or all 3 bricks to light ...the flame goes out i cleaned the bricks with air cleaner but to no change????
i think it might be the part the knob is on that switches it from 1 to 2 to 3 bricks not sure what it is called maybe a regulator of some sort.... anyone have ever had this happen and what can be done thanks bill
I have the same htr in Mich. & have worked on gas htrs.for many years.
Does the flame go out when you let go of the button to lite it?
If it does, then the thermocouple is bad.
If the flame stays on, but goes out when you turn the dial,
the gas regulator is bad.
Probably a little more expensive to buy new then to fix it.
Posted on Nov 22, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 28, 2017 | Empire Heating & Cooling
Jan 02, 2017 | Empire Heating & Cooling
Dec 14, 2015 | Heating & Cooling
Apr 07, 2011 | Stoves Heating & Cooling
Nov 28, 2010 | Reddy Heater RLP100 Portable Forced Air...
Oct 30, 2009 | Empire Hight Efficient Direct Vent Wall...
Oct 17, 2009 | Reddy Heater RLP100 Portable Forced Air...
Oct 04, 2008 | Reddy Heater RLP100 Portable Forced Air...
Aug 23, 2008 | Heating & Cooling
Aug 02, 2013 | Reddy Heater RLP100 Portable Forced Air...
703 people viewed this question
Usually answered in minutes!