Question about Intertherm Heating & Cooling
I have an intertherm unit for my mobile home and the heat went out on us. The ac seems to work fine, but no heat. I can switch the thermostat for the heater from the auto to on position, and it does blow air, but the air is luke warm. When I turn the heat on with the switch in auto position, nothing happens except a clicking noise and no air comes out, hot or not.
The clicking noise appears to be the igniter. Since it is not getting gas for some reason it will not operate and will shut down. This could be due to the burners being dirty or it could be a bad gas valve or it could be in the electronic mudule. Make sure there is gas coming into the home to the gas valve.Since you hear the igniter operating , for the time being we will assume it is ok. Clean the burners with a wire brush. Make sure they are clean. When reinstalling the burner. Make sure the igniter is directly over one of the burners in the path that the gas will take. This is important. Before attempting any repairs make sure you understand what to do and what not to do. Gas furnaces can be vary dangerous. If this is something you are not absolutely sure you can do. Get a qualified service man to repair and service the unit.You can get a qualified service man right here on this site for your area. I hope I have been of some help to you.
Posted on Nov 19, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 24, 2014 | Dometic Rooftop RV Air Conditioner
Feb 13, 2012 | Intertherm Heating & Cooling
Nov 02, 2011 | Intertherm P3RA-048K Air Conditioner
Jan 02, 2011 | Intertherm P3RA-048K Air Conditioner
Dec 13, 2010 | Intertherm P3RA-036K Air Conditioner
Aug 09, 2010 | Intertherm P3RA-036K Air Conditioner
Apr 30, 2009 | Heating & Cooling
Mar 14, 2009 | Heating & Cooling
Dec 21, 2008 | Heating & Cooling
Jan 15, 2008 | Intertherm P3RA-048K Air Conditioner
268 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: