Question about Reddy Heater-40,000 BTU Kerosene w/T'stat
The heater started find , but after releasing the automatic control value after the 30 seconds the heater will not stay on.
Not that it matters, but I just had a similiar problem with an RLP35. It would stay on only as long as you held the pilot button in. Did all of the checks and ultimately found that the problem was debris, maybe a spider web in the fuel tube. The flame before cleaning was not big enough to reach the thermocouple. After cleaning, the thing just purred. They offer the same advice for BBQ's each season to make sure you clean out the fuel tubes. Hope it helps--I have an extra thermocouple now if someone wants to buy it!!!!!!!!!!
Posted on Nov 20, 2008
Heater will run as long as the control valve is pressed.
According to DESA test these parts. NOTE: Not all heaters are equipped with
Turn off gas supply. Remove thermocouple
from gas valve. Using a digital
multi-meter set to the lowest DC millivolt
setting (meter needs to have alligator clips
on ends of leads), clip black lead to the
very tip of thermocouple (end removed
from valve). Clip red lead to the outer casing
of thermocouple for ground. Relight
unit output should be between 18 and 28
Turn off gas supply. Remove bottom of
base (if equipped). Relay is a normally
open circuit between terminals 4 and 6
which closes when current is supplied.
Using a digital multi-meter measure the
resistance. With no power to unit, resistance
between terminals 4 and 6 is open
circuit or no resistance. Apply power to
relay. Resistance between terminals 4 and
6 should be less than 100 mili ohms.
Posted on Nov 19, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 12, 2011 | Reddy Heater-30-55,000 BTU Variable
Here are a couple of tips that I wrote that tell you how to troubleshoot a Torpedo or Reddy heater...
Reddy Heater - Troubleshooting Torpedo Heaters
Dec 20, 2010 | Reddy Heater-30-55,000 BTU Variable
Oct 21, 2010 | Reddy Heater RLP100 Portable Forced Air...
Jan 27, 2010 | Reddy HD30 Heater
Jan 31, 2009 | Reddy Heater-30-55,000 BTU Variable
Oct 26, 2007 | Reddy Heater-30,000 BTU Propane Forced-Air...
160 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: