- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
what's happened here is the cm61 ng and the reciver box have lost there connection you will have to "rebind" them then it will be fine -
THE BINDING OPERATION DESCRIBED BELOW IS REQUIRED IF: ·Any of the system components (room unit or relay box) are replaced ·HC60NG has incorrect or no binding data stored (e.g. when pre-bound system pack components have been mismatched) ·Interference with the RF signal has caused a communication failure During the binding procedure keep approximately 1m distance between the room unit and the HC60NG 1Turn off mains supply to HC60NG for 10 seconds.Re-connect supply. 2Press and hold the HC60NG push button for 15 seconds to reset previously stored data.The red LED will start to flash at 0.1 s on/0.9 s off.Release the push button. 3Press and hold the HC60NG push button for 5 seconds to enter the binding mode.Red LED flashing at 0.5 s on/0.5 off confirms the binding mode has been entered. 4Move the CM67NG slider to the OFF position (CM61 push the OFF button) and press the TEMP ,TEMP and PROG 1 buttons together.The CM61/67NG will display InSt. 5Press the i button to send the binding signal.The red LED is switched off on the receiver box to confirm the successful binding operation.If the red light still flashes push the repeat steps 1-3 and press the the i button until binding is successful.
The problem is that the 2 units are "not speaking to each other". this could be caused by low batteries or a loss in signal caused by a powercut or an objection in the way of the 2 units.
first you need to turn the power off to the r666od (or otherwise known as the HC60NG) for 10 secs, then turn back on. then hold the grey button in for 15 secs. release then hold in for a further 5 secs.
go to the honeywell cm61 press the off button. hold temp up. temp down and prog 1 in for 3 secs until the dipslay goes to INST. at this point release all 3 buttons then press the i button until a beacon starts flashing.
this is now the end to your problem.
N.B the reason the green light was on is because the man override button will have been pressed.