Question about Honeywell Programmable Thermostat Heater
Green light on and red light flashing
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
I think I've done it - but don't take this as absolute truth.
For the Honeywell T6360B the original Potterton wiring should be rewired as follows:
Brown [Live] goes to terminal 1; Blue [neutral] goes to Terminal 2 and the yellow/green [which is not an earth but a switched live - i.e. gives live to the heating system when the thermostat clicks in] goes to terminal 3.
Obviously all done with the power isolated and when it was switched back on we had heating again :o)
It's been on over two hours now and all seems fine.
Posted on Feb 16, 2008
SOURCE: honeywell thermostat
I had the same problem and decided to take a chance and call honeywell customer support. I am shocked, they solved my problem! At least in my situation we found that the blue wire ran the compressor. Instead of hooking up to "blue" on the thermostat, we hooked it up to "white." It works wonderfully now.
Posted on Apr 25, 2009
red goes to RC and RH, White goes to W, Green goes to G and Blue goes to Y. iam assuming on the old tstat that Red whent to R White went to W Green went to G and Blue went to Y
Posted on Sep 20, 2009
Testimonial: "Thanks! Worked out great!"
you have to go down to your furnace and follow the thermostat wire ...it connects to a terminal strip or fan centre...the color doesn;t really matter...installers mix and match all the time....look at the furnace wiring and mark it down...Red on "R"...Green on "Y" whatever it is...and connect it accordingly upstairs...if you only have 4 thermostat wires downstairs you will need a jumper wire between RH and RC...if you have 5 wires you will see 2 wires on "R" at the furnace.,...and connect either to RH and RC at the thermostat
Posted on Nov 01, 2009
Tips for a great answer:
Feb 07, 2015 | Heating & Cooling
Jul 21, 2014 | Honeywell Ademco / GSMVLP-KT - GSM Radio...
May 17, 2011 | Honeywell Heat/Cool Thermostat
Aug 30, 2010 | Heating & Cooling
Oct 31, 2009 | Honeywell Programmable Thermostat Heater
Oct 08, 2009 | Honeywell Electronic Programmable...
Feb 15, 2009 | Honeywell Programmable Thermostat Heater
Feb 29, 2008 | Honeywell Programmable Thermostat Heater
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
167 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: