Question about Electrical Supplies
When running on auto sounds like it isnt getting enough fuel
You didn't say, so I'm assuming that this is an LP Vapor fueled Home Standby generator. The bottom line to these things is that if it sounds like a fuel problem it almost always is one.
1 - Check for leaky fuel supply plumbing.
2 - Check the fuel pressure at the input side of the demand regulator inside the generator, it needs to be something like 11 inches of water all the time. My Generac/Guardian training came with a nifty manometer just for this purpose. If you can't get a manometer your LP supplier should be able to come and make this measurement for you. If you aren't comfortable with adjusting the gas pressure you should call them anyway.
3 - Change the spark plugs. This isn't all that common a problem, but it's cheap compared to changing the demand regulator.
4 - Check/replace the demand regulator inside the generator. This part controls gas flow rate rather than gas pressure so if the diaphram in there gets sticky or leaky you can have fuel problems.
Posted on Nov 29, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 04, 2014 | 2001 Jaguar S-Type
Feb 09, 2018 | Cars & Trucks
Aug 10, 2013 | Garden
Jan 01, 2013 | 1990 Geo Prizm
Mar 29, 2011 | kawasaki ZX-9R Ninja Motorcycles
Nov 03, 2009 | Master Heaters MASTER HONDA POWERED...
Sep 01, 2009 | 1984 Ford Ranger
Mar 13, 2009 | 2005 kawasaki VN 800 Vulcan Classic
Jan 31, 2009 | 1994 kawasaki ZZR 1100
Aug 17, 2018 | Electrical Supplies
210 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: