- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
the bushing or the bearing in the motor may have already worn out. or may need some lubrication. the rotor is trying to turn but it's stiff and won't continue to turn. dont continue to turn on if it wont spin otherwise you'll damage the motor further. it might also be the busted capacitor "if it has"
The sound is from the compressor high side pressure exceeding design limits due to the fan not operating, the fan pulls air across the coil to remove heat from the freon which keeps the pressure down. The capacitor or fan motor may be bad. Need to open unit panel and visually inspect the capacitor for swelling, (rounded top should be flat) where the wires connect. Also use meter to test mfd of capacitor. May only need capacitor replacement, most common failure on this unit. If not corrected damage can be done to the compressor due to overheating.
You may have a bad condenser fan motor or a bad capacitor for that motor. If the compressor is running in the outside unit but the fan is not then it is most likely one of those two components that has failed. Consider calling a service tech to test it and see where the problem is.