Question about Coleman Propane Forced Air Heater w/Electronic Ignition (50,000-80,000 BTU)
I bought an older moble home and the furnace is newer but has not been used for 3 years. I rewired it to breaker box but blower will not come on. I have not hooked gas up yet till I can find problem. Does it need the gas on before it will come on?
I'm not a furnace technician. But I have worked on several Coleman trailer furnaces. So keep in mind that my terminology might not be exactly correct. But I think I can help you.
I don't know what model you are running, but most of them run pretty much the same. You have a four basic components to check. Thermostat; Ignition Control Module; Pressure Switch; and which ever of the following that you have (Glow plug, Electronic ignition, Pilot Light).
I'm assuming that you are referring to the blower as the "Rat wheel blower" (round wheel looking thing with fins on it). If my assumption is correct and if the power from the breaker box to the furnace junction box (Probably with a on and off switch on top or side), than when you give it power (from breaker box and turn thermostat up) the fan (not blower) comes on. If it doesn't there is a probably a problem with your Thermostat or Ignition Module. If it does come on and your glow plug or you igniter tries to work. Than yes, you are correct, you have to have gas pressure to let the pressure switch know that there is adequate gas supply pressure (gas- 5 to 7 W.C, propane 11 to 13 W.C). The reason for this is if the Pressure Switch doesn't feel the correct pressure. It thinks you have a leak and won't release gas for ignition. After you turn the gas on. If the furnace doesn't ignite. Make sure the Thermostat is definitely wired properly. Now we are down to one of three problems. If the Glow Plug, Electronic Ignition, or pilot light are working properly. Than we are down one of two problems. The Ignition Module or Pressure Switch. Check pressure on the Pressure Switch. If yuou don't smell gas it is probably OK. But it is best if you use a manometer. I have rarely found Pressure Switches bad. Normally if I get to that step. It is the Ignition Module. The Ignition Module kind of like the brain of the furnace. It is located behind one of your front panels. It will have approximately 10 wires going to it. Some will be going to the Thermostat, some to the Glow plug (Igniter), some to the Pressure Switch, and some going to the blower.
I have probably said more than you need to know. If I did I apologize. But to wrap it up. You were probably correct. You definitely need gas for the blower to kick on. The furnace has to light and heat up before the blower will Start. Not to keep rattling, but to check to see if the blower motor will run. Is to switch the Thermostat from "auto" to "run".
Posted on Nov 23, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 02, 2017 | Gibson Heating & Cooling
Jan 17, 2016 | Heating & Cooling
Sep 29, 2015 | Heating & Cooling
Mar 07, 2015 | Goodman Heating & Cooling
Mar 01, 2013 | Lennox Heating & Cooling
Jan 04, 2013 | Coleman Mobile Modular Home Electric...
Jan 15, 2012 | Rheem Heating & Cooling
Feb 14, 2011 | Tools & Hardware - Others
Oct 23, 2010 | Heating & Cooling
May 15, 2014 | Coleman Propane Forced Air Heater...
796 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: