Question about Siemens 200 Amp Main Breaker 30 Spaces 40 Circuits
Only inter mitten breakers working in the box. Its not the breakers, replaced them. Not the connection on the post. Do not see any visible problems, pulled breakers and looked at bus and nothing looked suspicious. Do I need a new breaker box this one is a Siemens 200 amp and only about five years old.
Did you ever get it fixed?
i have the same problem you describe.
Posted on Jan 01, 2009
POSSIBLE THE BREAKERS ARE WORKING AND THE NEUTRAL IS OPEN , MOVE ONE OF THE WIRES FROM A BREAKER YOU KNOW TO BE WORKING ,THEN REPLACE IT WITH ONE THAT IS NOT IF CIRCUIT COMES UP THE BREAKER IS NOT WORKING IF IT DOES NOT THE PROBLEM IS THE NEUTRAL WIRE FOR THAT CIRCUIT MOST WILL BE WHITE WIRES ENTERING PANEL , IF THE BREAKER ALTERNATE WORKING MOVING DOWN THE BUSS SAY #1 WORKS #2DOESNT #3WORKS #4 DOESNT ECT ON THE SAME SIDE OF PANEL YOU HAVE A DEAD BUSS ,CAUSED BY BAD MAIN OR THE FEED FROM METER BASE ,THEN YOU SHOULD CALL ELECTRICIAN
Posted on Nov 23, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 10, 2015 | Electrical Supplies
Oct 27, 2012 | Electrical Supplies
Feb 18, 2011 | Cutler Hammer 100 Amp Main Breaker...
Feb 14, 2011 | Cutler Hammer "WESTINGHOUSE" MAIN DOUBLE...
Dec 29, 2010 | Electrical Supplies
Dec 05, 2010 | GE Electrical Supplies
Oct 24, 2010 | Gb Electrical 100 Amp GE Load Center
Oct 18, 2010 | Siemens 2 pole 20 amp breaker
Sep 14, 2010 | Square D Qo 100 Amp Breaker Box Qo120m100...
Mar 06, 2009 | Connecticut Electric & SWITCH UBIP130...
Sep 23, 2011 | Siemens 200 Amp Main Breaker 30 Spaces 40...
381 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: