Question about Intertherm Heating & Cooling
Upon starting my intertherm furnace for the first time the fan runs but won't ignite ,the indicator light flashes twice,indicating a "open pressure switch".What does this mean? and how do I rectify?
Downstream of your fan discharge there is a little plastic assy. most likely that will have a pickup tube and a piece of vinyl or latex tubing attached. First check to make sure that the pick up tube and/or tubing does not have a restriction. If it is clean use an ohm meter to read resistance across the switch to verify it is operating.
Posted on Nov 15, 2008
My gas furnace wont kick on when it has been off for awile, we have replaced the thermostate and checked eveything else. Once we gett it going it works but wont kick in once the temp drops
Posted on Nov 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 06, 2015 | Intertherm Heating & Cooling
Oct 26, 2013 | Intertherm 56000 Btu Gas Furnace
Dec 21, 2012 | Heating & Cooling
Nov 05, 2011 | Intertherm P3RA-048K Air Conditioner
Feb 23, 2011 | Intertherm Heating & Cooling
Oct 18, 2010 | Honeywell Heating & Cooling
Feb 09, 2009 | Intertherm P3RA-048K Air Conditioner
Jan 18, 2009 | Intertherm P3RA-048K Air Conditioner
Aug 27, 2008 | Intertherm Heating & Cooling
872 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: