Question about Honeywell Heating & Cooling
Wires for thermostat control circuits are normally color coded. Check for proper connections at the furnace and connect the same colored wires that you find at the furnace to the like lettered terminals on the new thermostat. R to R, W to W , Y to Y , ans G to G. R is for power to the thermostat, W is for heating, Y is for cooling and G is for furnace fan operation.
Posted on Nov 15, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 11, 2015 | Honeywell CT31A - Economy Heat/Cool...
on Jan 16, 2010 | Heating & Cooling
Feb 06, 2014 | Honeywell RTH3100C - Digital Heat Pump...
Oct 20, 2013 | Haier 2.0 Ton Multi-position Air Handler...
Sep 06, 2011 | Honeywell Heating & Cooling
Dec 31, 2010 | Honeywell Heating & Cooling
Jan 21, 2009 | Heating & Cooling
Sep 30, 2008 | Heating & Cooling
Jun 14, 2008 | Ruud UBHC Air Conditioner
Jan 15, 2017 | Honeywell Heating & Cooling
87 people viewed this question
Usually answered in minutes!