Question about Heating & Cooling
Not familiar with that particular model but on virtually every type and style of furnace i have worked on in the last 21 years. the fan is delayed. usually the burner lights then 3 to 5 minutes later after the heat exchanger has gotten nice and hot the fan comes on and blows nice and hot air. on old furnaces there was and is a switch usually on the upper right side of the furnace bulkhead that has a spring like device that heats up and rotates till it makes a set of contacts that turn the fan on. if it gets to hot the set of contacts breaks the power to the gas valve and shuts down the burner. as the furnace cools down on shut off there is a third set of contacts that open to turn off the fan so you don't get a draft. sometimes the stat can be wired up wrong, and it will bring the fan on right away ,and air will be cool and drafty till furnace catches up.
Posted on Nov 13, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 17, 2017 | Heating & Cooling
Nov 08, 2016 | Heating & Cooling
Jun 09, 2014 | Coleman Propane Forced Air Heater...
Dec 07, 2012 | Heating & Cooling
Jan 11, 2011 | American Standard Heating & Cooling
Dec 17, 2008 | Coleman Propane Forced Air Heater...
Dec 13, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
159 people viewed this question
Usually answered in minutes!