Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
I have a Carrier Weather Maker 8000 that has refused to start this winter. On checking the error codes comes out to be 21 which states gas blockage. One of the suggestion was to shut off the heater and let it reset which has not helped. (Left it Off for the whole night but when started the next morning, it still did not start. The ignitor comes on but since gas fails to come, it glows for few seconds and then turns off. Any suggestion would be appreciated.
I checked again today and from what I can gather, the error code is 12 and not 21. The error code 12 translates to "blower on after power up" or "R-W Closed". I have no idea what all this means. Any help would be appreciated.
Either the gas valve is not opening or your not getting gas to the furnace. also the gas valve won't open unless the draft motor comes on. if the ignitor is trying to light, but there's no gas, it might be a bad gas valve. i would call your closest NATE certified contractor
Posted on Nov 17, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 12, 2013 | Heating & Cooling
Oct 03, 2011 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 22, 2017 | Carrier XHB123D X/Y Series Heat/Cool Air...
Feb 20, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 04, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 30, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 11, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 10, 2008 | Heating & Cooling
Nov 23, 2007 | Carrier XHB123D X/Y Series Heat/Cool Air...
979 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: