Question about Heating & Cooling
Here is the sequence I see.
I ask for heat. The combustion exhaust fan comes on. The ignighter glows. As the glow fades, I hear the gas valve clicking open but as if it is too late, it turns off, never firing the burners. I smell a hint of propane at this point.
However, if when I hear the valve kick on I BLOW THE GAS THROUGH, THE BURNERS IGNITE! - and the system stays on until the demand for heat is satisfied. But, next time, If I am not there to blow on it, the system attampts to light 3 x and on the last fail, the house blower fan comes on. I can only turn it off by cutting current to the unit. This also re-sets the unit to go through another 3 cycle attempt to fire.
It is as if the igniter and the gas valve are no longer in synck.
The error code is 2 flashes - system lockout (no flame) check line polarity.
Again, if I blow the gas to the fading glow of the igniter, the unit fires and continues to work just fine so I guess all the limiters and safery circuits are functional
The unit worked fine for years. Then a few times, we just turned the power off and it fired the next time. Now it seems the delay got worse.
Is there a way to re-set the cirquit board? any suggestions or revelations on what is wrong? Any questions to clarify my problem? Please ask. I have a multi-tester and can read wiring diagrams and usually manage to fix things myself. This time I need help. Thank you in advance for providing it.
Put your hand on the gas valve and see if the click of the valve is opening just before the ignitor goes off if it does your valve is going bad
Posted on Nov 13, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 26, 2015 | Heating & Cooling
Apr 19, 2015 | Dryers
Nov 23, 2013 | Maytag Neptune MDG6800 Gas Dryer
May 19, 2011 | Maytag Neptune MDG9700A Gas Dryer
Dec 29, 2009 | Heating & Cooling
Dec 16, 2009 | Goodman GMS90703BXA Heater
Nov 24, 2009 | Heating & Cooling
Oct 29, 2009 | Heating & Cooling
Dec 04, 2008 | Goodman GMS90703BXA Heater
Nov 08, 2008 | Goodman GDS80703ANA Open Flame Mid-Size...
Jan 22, 2018 | Heating & Cooling
123 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: