Question about Cozy Enclosed Front Console Heater 70,000 btuh Natural Gas
I have a Cozy VC701A-R and It will light and burn fine for a while, but the pilot light will go out when the thermostat cuts off the burners. What can I do to solve this problem?
The VC701 has a safety switch located on the back of he heater that may be tripping after the call for heat is satisfied. Check that there is a good draft by testing with a match. Make sure the flame is drawn toward the vent system when the unit is off and cooling down. Check it at the draft diverter located below where the vent pipe is attached. It is a box with an open bottom. If the draft is not pulling air toward the vent system, the heat from the cooling heater will trigger the safety switch and shut off the pilot. You may have to raise the vent pipe to establish a draft.
Posted on Sep 24, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 30, 2017 | Cozy Heating & Cooling
Nov 24, 2016 | Cozy Heating & Cooling
Feb 24, 2011 | Heating & Cooling
Jan 24, 2011 | Cozy Enclosed Front Console Heater 70,000...
Nov 27, 2010 | Cozy (W352E) Heater
Nov 07, 2010 | Cozy (W352E) Heater
Jan 28, 2009 | Heating & Cooling
Dec 27, 2008 | Cozy Enclosed Front Console Heater 70,000...
Nov 15, 2012 | Cozy Enclosed Front Console Heater 70,000...
Nov 12, 2012 | Cozy Enclosed Front Console Heater 70,000...
Dec 16, 2010 | Cozy Enclosed Front Console Heater 70,000...
406 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: