Question about Intertherm Heating & Cooling
This wire is powered by a small transformer, and delivers low voltage to energize the colenoid that turns on the ac unit. Turn the ac on from the inside. Then check if it is getting the voltage. Usually 24V AC. If not getting the voltage, go to the attic where the evaporator assemble is and locate that small transformer. It may have shorted out. You don't have to get an exactly the same one, but get one with same rating. They are rated with input voltage, output voltage, and ampere. They are usually 800mA. The input is usually 120 volts ac and output is 24 volts ac. It should say it on the transformer itself.
Posted on Aug 15, 2009
There is nothing you can do if they want heat....the convection currents are what heats the rooms....hot air naturally rises and the cooler air falls to the floor... can't change nature...
Posted on Dec 12, 2010
Tips for a great answer:
Jan 08, 2017 | Honeywell Heating & Cooling
Jan 05, 2017 | Reddy Heating & Cooling
Jan 04, 2017 | All-Pro Heating & Cooling
Jan 04, 2017 | Heating & Cooling
Dec 22, 2016 | Kenwood EW7507EK Oil Radiator
Sep 04, 2016 | Heating & Cooling
Jan 11, 2015 | Heating & Cooling
Dec 25, 2014 | Heating & Cooling
Oct 07, 2014 | Heating & Cooling
Sep 24, 2012 | Heating & Cooling
105 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: