Question about Haier Energy Star ESA3183 Air Conditioner
My furnace has two double pole breakers, The top double pole breaker died and needs replaced. Evidently, this breaker does not snap in like some breakers. How do I get the top breaker out? I notice there are 4 screws holding both breakers to a plate.
Thank you for any help you can offer.
Shut the breaker off,loosen the screws and the breaker will lift off the rail,loosen the wires on the breaker,bring breaker to store when buying replacement,snap new breaker in place on rail,make sure lugs are tight on new breaker,turn breaker on
Posted on Nov 16, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 15, 2014 | GE 20 Amp 1 In Double Pole Circuit Breaker...
Jan 24, 2011 | Siemens 20 Amp Single Pole Breaker 120/240...
Jan 20, 2011 | Electric Circuit Breaker Kit for Furnace
Jan 17, 2010 | Connecticut Electric & Switch Thqp115...
Jun 29, 2009 | Square QO 30 Amp Double Pole Circuit...
May 31, 2009 | Hobart H600 Stand Mixer
Feb 11, 2009 | Connecticut Electric & SWITCH UBIP130...
Dec 01, 2008 | Siemens 2 single pole 15 amp breaker
150 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: