Question about Heating & Cooling
The cm67ng has a feature which attempts to get the temperature to the
desired point before the actual time you set. In reality this "feature"
just makes the device turn on and off randomly in a really bemusing
fashion. You can turn this off with the following:
1, Set timer mode to "OFF"
2, Hold down "Info i" and press "prog 3" and "prog 4" together. Display Should show a spanner in the left hand corner.
3, press "prog 2"
4, repeated press "clock +" till the characters in the display after the colon read "OP" (the number before the colon seems to vary with model).
5, Press the "temp down" button. The 1 in the right hand of the display should become a 0.
6, Press the "info i" button to save your changes.
7, Switch the mode back to auto, the timer should now behave normally.
You should note that a number of other parameters can be changed in this service mode. Some of which could probably do bad things to your central heating system if set incorrectly.. So this is at your own risk! Either way it's best to read the installation manual before attempting to change anything:
Posted on Nov 10, 2009
I had the same problem. The issue is that if you set the temperature to be 20 degrees at 8.00, it will ensure that the temperature is at 20 degrees at this time. I.e. it will set the boiler going well before this time. I was frequently woken up by the heating being on in the middle of the night. My solution works perfectly for me as I do not have complex requirements. I simply set the timer to be at say 10 degrees at 11.00 pm and again at 8.00 am, and then at 20 degrees at 8.20. This means that between 11.00 om & 8.00am is will maintain 10 degrees, but come 8.01 will be working flat out to try to achieve 20 degrees by 8.20!!
It works for me.
Posted on Sep 02, 2009
If it comes on at 4am instead of 7am try advancing the on time by 3hrs to 10.00am - this seems to work - until someone comes up with a "proper solution."
Posted on Jan 24, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Oct 21, 2017 | Heating & Cooling
Welcome to fixya
I have a solution for this
Press Ok, Accept or replay so we may get started
Your pre-solution is coming up shortly
REPLY OR LEAVE COMMENT TO CONFIRM YOU RECEIVED THIS EMAIL
My name is Bruce
Jan 17, 2011 | Honeywell Programmable Thermostat Heater
Dec 08, 2010 | Honeywell Programmable Thermostat Heater
Apr 29, 2017 | Honeywell Programmable Thermostat Heater
Sep 13, 2010 | Honeywell Focus 6300B 5-2 Days...
Dec 20, 2009 | Honeywell Programmable Thermostat Heater
Nov 30, 2009 | Honeywell Programmable Thermostat Heater
Oct 31, 2009 | Honeywell Programmable Thermostat Heater
Feb 29, 2008 | Honeywell Programmable Thermostat Heater
2,454 people viewed this question
Usually answered in minutes!