- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Under normal circumstances, NO!
Black is normally power in to a box and to a switch. The switch controls the power out to the red line and most likely the blue line.
White is always circuit neutral (ground).
Your power will most likely come in via black and then go to the lights on either red or blue and to the fan on the other wire, either red or blue, the color you did NOT use for the lights. Some place you should also have a bare or green wire that would act as equipment ground, connecting to the metal of the box.
The usuall wiring for a ceiling fan is black to black, white to white , and red house wire to the other fan wire, sometimes blue. If you only have two wires from the ceiling, then it is still white to white and black to black, but add the other fan wire to the black wires ..
Try this, connect green wire to bare wire. Connect both black (power) wires to black wire in the box. Connect the blue wire to the button for the lights, and the red wire with the strip to the button for the fan, and the common for the buttons to the white wire.
My fan does not have a reverse switch for sure so I scoured the net and got no real answer. I did come accross a comment that said that it worked internally at the remote box in ceiling. Here is how I finally figured it out after about 6 months of searching. Put the fan on high, Turn wall switch OFF, Hold the HI button on remote, Turn switch back on. IT WORKS!!!!!!!!!!!!! Sparq
Some fans will not operate without the remote, however, I'm not sure if the Hampton Bay brand is one of these or not. Below is how you will bypass the remote if the fan will operate without the remote.
You can try disconnecting the receiver in the canopy of the van (the cover that fits snug to the ceiling) once you have shut off the power source remove the canopy and find the remote receiver.
Most likely it will be a rectangular box with white, black, and blue or red wires attached. Disconnect all wires from the receiver and lay it to the side.
Now reconnect the wires directly to the fan, white to white, black to black, if you have a red wire (or a second black wire) in the ceiling box connect it to the blue wire from the fan.
If you do not have a red wire (or second black wire) in the ceiling box, connect the black and blue wire from the fan to the single black wire in the ceiling box. This method will require you to pull the chain to operate the fan separately.
your remote modual should have two or three wires coming from the unit on one side to go to the fixture and three on the other to hook it to power , the three should be to connect to the black (power), the white (Neutral) and green (ground), now the unit has power. The two or three coming from the other side should be a white and two other colors or two the same , black, red, or blue, The white connects to the fan white and the other two go to, one the fan and two the light. Any questions E-mail me...hwyhmmr hotmail
If you don't want the to use the remote you don't have to, but you don't have enough wires to switch the upper light, the lower light, and the fan. You can, however, switch the upper and lower lights together if that's okay. In order to do that you'd connect the white from the ceiling box to the white (neutral) on the fan, then the green from the ceiling box to any green(ground) wires on the fan, then the black from the ceiling box to the black(motor) from the fan, then the red from the ceiling box to the blue and orange (lights) from the fan. I'm assuming that the black and red in the ceiling box are also in the switch box where the fan/light control switch is going. Those are the ones you'll connect to the controller.
in your ceiling box should be three wires. a red goes to the three way switches, a black goes to the hot and the white is the neutral. the fan wires are black, blue and white. since you have a remote, connect the [fan] blue & black together with the [line] black. connect all white wires together. the remote will now ramp up your lights from off to full on and the fan remote will let you choose lo med high and off. just tape up the red wire in the box.