Question about Goodman GDS80904BNA Open Flame Heater
That pressure switch closes for a run condition. check for continuity between the plugs on it with the induction fan running. If its closed, change the board if not change the switch.
The switch will tell you its pressure rating on the label and its best to just use the same rating. Easiest to get it from a Goodman Parts Supplier. You can order it on the internet, should have a part number on the label or just use the model and serial of the furnace. Locally you will probably have to buy it from someone in the trade.
Posted on Nov 18, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 04, 2013 | Coleman Heating & Cooling
Nov 29, 2011 | Goodman Heating & Cooling
Oct 18, 2011 | Goodman GMS90703BXA Heater
Mar 15, 2011 | Coleman Heating & Cooling
Feb 03, 2011 | Goodman Heating & Cooling
Dec 02, 2010 | Heating & Cooling
Nov 16, 2009 | Coleman Propane Forced Air Heater...
Feb 15, 2009 | Goodman GMS90703BXA Heater
110 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: