Question about Aprilaire 1120 Humidifier
Kurt, a couple of things you can check. First when you turn the humidistat do you hear a click from the solenoid? This would indicate that you are in fact getting power. Check the saddle valve from the supply. Turn it in and out to make sure it is not clogged. You should have a inline strainer on the inlet side of the valve. Make sure it is not clogged with deposits. On the discharge side of the valve should be an oriface, make sure that is clog free. If you have an meter you can check for power at the soleniod or pull the harness off and ohm it. Should show continuity. Catriver...post back.
Posted on Oct 15, 2006
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Feb 12, 2015 | Honeywell Humidifiers
Nov 10, 2013 | Honeywell HE360A1027 Whole House...
Nov 26, 2011 | Aprilaire 700 Humidifier
Sep 17, 2011 | Essick Air Humidifiers
Jul 06, 2011 | General Filters 1042-LH Humidifier
May 07, 2011 | Kenmore Humidifiers
Dec 28, 2010 | Honeywell 360B Humidifier
Dec 21, 2010 | Aprilaire 700 Humidifier
Dec 22, 2009 | Aprilaire 700 Humidifier
Jan 11, 2009 | Aprilaire 600 Humidifier
Apr 01, 2009 | Aprilaire 1120 Humidifier
219 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: