Question about American Standard Colony 3275.505 099 Chrome/Brass Mixage Soft Two-Handle B...
Let's start with assuming nothing okay. There may have been two cold water lines ran to the faucet at time of a repair in error. The stop under the sink could be turned off. The supply pipes may be connected backwards making cold hot and hot cold.The stem on a single handle model may be installed incorrectly. A piece of trash or part of the valve seat- if an older two handle type - may be obstructing the water flow. You could also have a ruptured pipe under the slab.
Let's start with the worst case scenario first- a break in the piping system. Shut all water off inside the house as well as any outside faucets etcetera that may cuse the usage of water. Go to the hot water heater and close the hot water valve. Now go to the water meter and see if the meter is moving- it should be stationary. If you use a pump check for a loss in pressure at the bladder tank. If all is good go and open the hot water valve and check again at the meter. If the meter is moving there is a break in the line. If not we will proceed.
Now go to the sink you have issue with and check the stops to see that they are turned on. If so turn them both off and get you a bucket, towel, flashlight and a basin wrench and remove the hot water supply line. Once you have this done bend the line into the bucket and turn the stop back on and see if you get hot water here. If not try the same with the other supply line. If neither produce hot water you more than likely have a cold line ran to both supplies. If you are able to get hot water than the issue is within the faucet. Re connect the supply lines and leave the stops off. Remove the stem from the faucet and turn the stop on a bit to flush out trsh and debris. If you have a stem that uses a valve seat - a small piece of rubber attached to the bottom of it by a screw- check to ensure that it is not missing parts of it that may get lodged in the valve itself. Assuming this is new house, to you anyway, it is also possible that the manner in which the hot water line to that appliance was ran from to far away from the water heater and requires a great deal of time before it reaches this appliance.
I hope this assists you to some degree and apologize for being longwinded. Thanks for using Fix Ya and if I can be of further assistance please let me know.
Posted on Nov 09, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 04, 2015 | Fleetwood 2014 Discovery 40G
Jul 21, 2014 | Itasca 2008 Ellipse 40WD
May 01, 2011 | Delta Faucet Bathroom Faucet - Delta 2...
Feb 19, 2011 | Price Pfister Single Lever Handle Faucet...
May 16, 2010 | Moen & One Handle Tub & Shower Faucet
Oct 07, 2009 | Kohler K-T10335-4-CP Lyntier Rite-temp...
Aug 01, 2009 | Home
Feb 01, 2009 | Moen 3175 Legend One Handle Shower Faucet...
173 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: