Question about Heating & Cooling
I had this trouble 2 years ago. . . . Air, blower work fine, when I turn on "Heat" it clicks a couple of quick times and wont start up the furnace. The system is only 5 years old .( i believe it was installed in july of 2004 , furnace, a/c lennox)
I've replace batteries and "reset" several time thinking the batteries were too low to start it up.
The thermostat was replace 2 years ago and now its doing it again. Any suggestions other than having to get them back out here would be helpful. Thank you .
I have a thermostat 9600 Robertshaw and I have to use the trip switch to start my furnace. Then it reaches the temperature and sometimes it will kick in by itself but majority of the time I have to trip it. I have changed the batteries cleaned the thermostat,and reset it. Is it time for a new thermostat and can I replace it myself. Thanks
Posted on Jan 16, 2009
Look under the cover where you change the batteries. find the common and the white wire. if you have it in heat and there is 24 volts batween w and common, then the stat is good and the problem lies in the furnace. checking in the furnace the power should arrive at the furnace control board or the common and white as 24 volts also. first to start is the forced draft motor, 120 volts. next the glow bar , 120 volts or ignitor arcs and then gas burner lights and heats up then the blower runs . whatever item fails to perform is your problem . check with meter where possible and if power goes in and item doesn't perform thats your problem. when the forced draft motor runs it closes a pressure switch usually to the upper right and then the board knows it can proceed to power glow bar or ignitor and light burner then open the gas valve for ignition. good luck
Posted on Nov 07, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 31, 2015 | Heating & Cooling
Jan 14, 2011 | Heating & Cooling
Dec 10, 2010 | Shaw Robert RS-9420 Thermostat
Sep 05, 2010 | Heating & Cooling
Jul 25, 2009 | Shaw Robert RS-9420 Thermostat
Jun 30, 2009 | Shaw Robert RS-9420 Thermostat
Jan 04, 2009 | Hunter Fan Company 5/1/1 Programmable...
Oct 22, 2008 | Goodman GMS90703BXA Heater
Jan 16, 2018 | Heating & Cooling
2,991 people viewed this question
Usually answered in minutes!