Question about Fahrenheat Electric Convector Baseboard Heater, 240 Volt
I would like to know if I wired my new heaters correctly went form power supply 20amp breaker 12/2 wire to thermostat from thermostat to first heater black and red wire pigtailed a second wire and ran it to the second heater pigtailed black and red with a second wire to the third heater. also hooked up ground wires in each of the units. Have I correctly wired these units together
Yes, you did a good job. Sounds like you paralled them. Which is right buuuut what size are these heaters. Add the wattage of all of the heaters and divide by 120 and that is how much current you will be using. On a 20 amp breaker you can only pull 16 amps safely. I think you will be way over unless the heaters are 600 watts each. You are allowed 1800 watts on a 20 amp circuit.
Posted on Nov 06, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 04, 2011 | Heating & Cooling
Apr 30, 2017 | Marley Electric Hydronic Baseboard Heater,...
Feb 23, 2010 | Kenmore 79383 Dual Fuel (Electric and Gas)...
Dec 09, 2009 | Sewing Machines
Jan 20, 2009 | Fahrenheat Electric Convector Baseboard...
Dec 14, 2008 | Fahrenheat Electric Convector Baseboard...
Aug 06, 2008 | Microwave Ovens
Jun 23, 2008 | Carrier Heating & Cooling
135 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: