Question about Electrical Supplies
My cord switch in my bathroom broke, it didn't click when pulled and the light remained permanently on, it was fitted by a qualified electrician. I bought a new one and replaced the broken one, it worked fine a couple of times then the same thing happened. I have a fan linked to the light switch and 4 different coloured wires which are red, blue, yellow and the earth. on the switch is L1, L2, COM and earth. please can you help and let me know if I am using the right switch and if there is a reason why both switches have broken in the same way.
There are two possibilities here,
1. it is a mechanical failure i.e a part of the linkage has broken leaving the switch in the on position, did you see anything obviously wrong with the old switch?
2. It is an electrical failure either overload or arcing when the switch is being operated sometimes welding the contacts together. This can happen if the light is a fluorescent tube or ring type, which in combination with the fan start up, can cause this situation. If this is the case you need a higher current rated switch.
Please remember to rate this solution.
Posted on Nov 03, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 24, 2013 | Dimplex Fx20ve 2kw Timer Wall Mounted...
Feb 16, 2012 | Duravit Home
Jan 22, 2011 | Solar 2-wire Pull Chain Light Switch For...
Apr 05, 2010 | Solar 2-wire Pull Chain Light Switch For...
Jan 12, 2010 | Solar 2-wire Pull Chain Light Switch For...
Oct 03, 2009 | Electrical Supplies
Sep 14, 2009 | Dryers
Oct 15, 2008 | Electrical Supplies
652 people viewed this question
Usually answered in minutes!