Question about Heating & Cooling
Hi, I just finished installing a Senville Mini Split HVAC unit. After evacuating the lines, I opened the valves on the outside unit, and turned on power. (The outside unit was supposed to be shipped with enough R410a to run the unit, with the lines supplied.) I didn't hear a great deal of hissing noise when I opened the line valves, so it could be low on R410a, but??? It shows an error code of E4, but there is no documentation with it to tell me what that code means. The compressor does not function on either heat or cool, but the blower does work on fan only mode. All the settings seem to turn on the correct lights on the panel, but it has this error code posted. Can anyone tell me what that code means? I suspect it's telling me it's low on R410a, but...
The model is: KFR-35GWZ/BM
Thanks in advance...
The E4 light on your system is saying there is a commiuntion problem between the inside unit and the outside heatpump unit.Make sure there are no loose wires and you wired it properly,The S wire is the commiuntion link wire make sure it is a solid run between both units.I had the same problem with my system and it was the s wire not making a good connection.
Posted on Apr 25, 2009
I have purchased over 45 units from GT-World and had a similar issue with one of the split air conditioner units last year. Visited http://www.gt-world.com/faq and found the solution to my problem. Most people install the inverter compressors them selfs and burn the board on the unit. Spoke to Jim at ext 25 and he was very helpful. Had the issue revolved within 48 hours.
10 bucks says orange rooseter installed the unit himself haha. Its not cool calling the good people @ gt-world crooks and shysters buddy.
Posted on Apr 23, 2010
I've spoken to the distributors tech. He says that the unit shuts down the condenser to protect the unit (E4 error code). He said some possible causes could be: 1. The condenser unit is in an atmosphere that is too hot (like in a garage without proper ventilation). 2. There is a leak (usually at the flare joints--feel around for a greasy type liquid). 3. Something electrical--check all the connections. I'm not sure if this'll help, but at least it's a place to start.
Posted on Feb 05, 2010
I have the same problem but GT World has been useless in helping. Despite importing the product these a$$hats don't even know what the error codes mean. I'm out two thousand dollars and have a useless piece of Shinco junk hanging on my wall. I'll never, ever, ever buy another Shinco product or anything at all from the shysters and crooks at GT World. Save yourself lots of grief and avoid Shinco and GT World.
Posted on Jan 03, 2010
I also have purchased a lot of Senville air conditioners from http://www.airconditioneroutlet.com/ and never had an error code appear. They have a support line you can find their number on the website they will be able to help you.
Posted on Aug 04, 2012
SOURCE: Senville Mini Split Error Code
thanks for your question, you will need a set of gauges on the unit to determine if the unit came precharged, if it didn't then you will need to vacuum down the unit, at least three times, after each time release a little 410a into the system them evacuate again, 410a is bad for drawing moisture, did you put an in-line filter dryer on as well ? after you find out about the freon level, then look at the name plate rating for amount of 410a needed, before adding the freon, use nitrogen to leak check the system, then weigh in the proper amount of 410a, unit should run really well after that, hope that helped, thanks again for your question, please feel free to come back if you have any more questions, thanks, mr.grzz
Posted on Jan 21, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 29, 2016 | Inverter Heating & Cooling
Sep 08, 2015 | Senville 24000 BTU Energy Star Ductless...
Jul 02, 2015 | Senville 24000 BTU Energy Star Ductless...
Dec 31, 2014 | Senville 18000Btu 21 Seer 12.5 EER...
Jul 26, 2014 | Samsung AQV12VBCN Vivace Mirror Finish...
Aug 24, 2013 | Heating & Cooling
Aug 22, 2013 | Senville 18000 BTU Energy Star Ductless...
Jan 21, 2009 | Heating & Cooling
3,735 people viewed this question
Usually answered in minutes!