Question about Ruud UBHC Air Conditioner
Either tstat sensativity setting is too high or possible low pressure switch. if you have had to add freon before and never located the leak it would possibly be low on freon again. If you have replaced the tstat you may need to adjust the settings .
Posted on Nov 24, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 08, 2016 | Ruud Heating & Cooling
Sep 29, 2012 | Ruud Heating & Cooling
Jul 27, 2011 | Ruud UBHC Air Conditioner
Jul 05, 2010 | Ruud Central System Air Conditioner
Feb 08, 2010 | Ruud UBHC Air Conditioner
Sep 28, 2009 | Ruud UBHC Air Conditioner
Aug 05, 2009 | Ruud Matching Split Air Conditioner
Aug 18, 2008 | Ruud UBHC Air Conditioner
97 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: