Question about Honeywell Heating & Cooling
SOURCE: I have a Vulcan/ILEC ducted
there is probably a sensor in the duct somewhere that is either fault or maybe quite dusty. be careful though it may have mains voltage at the terminals
Posted on Jul 10, 2008
Thanks for using FixYa. Perofrm this test--
Connect DATS Sensor to EMM-3 (optional).
a. Reconnect power to EMM-3.
b. If system is in Purge mode, press PURGE OVERRIDE on EMM3.
c. Verify SYSTEM LED is no longer flashing. This confirms proper DATS operation. (Flashing occurs in Idle and Fan modes only.)
Also see page# 9 & 10 from this link--
Honeywell EMM-3 zone controller
Please do accept the solution if the issue is resolved or else revert for further assistance.
Posted on Aug 28, 2009
For Trane sytems, B is your "Common" wire. O is your reversing valve relay, G is your fan, Y is your compressor contactor, R is Hot, Brown will not be used on your electronic tstat. X2 is your backup electric heaters. Without knowing what terminals are on your new tstat, I cannot offer more information than this. The installation manual may indicate what each terminal is controlling. I strongly suggest to write down ALL of the terminals and colors from your old t-stat and be sure to turn off the power to your air handler. Put the fan switch on your tstat to ON before turning off the power. Make sure the fan is running. Then turn the power off to your Air Handler. If your fan stops running, you have turned the power off to your tstat and are ready to start replacing it with your new tstat. I hope you find this helpful. Good Luck!!!
Posted on Feb 07, 2010
The # is on the BACK- yeah go figure, of the unit. Lift the front up from the bottom and it will come off (it goes back on). THEN you will see your number. Mine was a CT3611.
Posted on Apr 07, 2010
Tips for a great answer:
Dec 01, 2014 | Honeywell Heating & Cooling
Jul 08, 2014 | Honeywell Heating & Cooling
Sep 01, 2011 | Honeywell Heating & Cooling
Mar 10, 2010 | Honeywell Heating & Cooling
Oct 01, 2009 | Honeywell Electronic Programmable...
May 21, 2008 | Honeywell Heating & Cooling
100 people viewed this question
Usually answered in minutes!