Question about Honeywell Air Conditioners
SOURCE: I have a Vulcan/ILEC ducted
there is probably a sensor in the duct somewhere that is either fault or maybe quite dusty. be careful though it may have mains voltage at the terminals
Posted on Jul 10, 2008
Thanks for using FixYa. Perofrm this test--
Connect DATS Sensor to EMM-3 (optional).
a. Reconnect power to EMM-3.
b. If system is in Purge mode, press PURGE OVERRIDE on EMM3.
c. Verify SYSTEM LED is no longer flashing. This confirms proper DATS operation. (Flashing occurs in Idle and Fan modes only.)
Also see page# 9 & 10 from this link--
Honeywell EMM-3 zone controller
Please do accept the solution if the issue is resolved or else revert for further assistance.
Posted on Aug 28, 2009
For Trane sytems, B is your "Common" wire. O is your reversing valve relay, G is your fan, Y is your compressor contactor, R is Hot, Brown will not be used on your electronic tstat. X2 is your backup electric heaters. Without knowing what terminals are on your new tstat, I cannot offer more information than this. The installation manual may indicate what each terminal is controlling. I strongly suggest to write down ALL of the terminals and colors from your old t-stat and be sure to turn off the power to your air handler. Put the fan switch on your tstat to ON before turning off the power. Make sure the fan is running. Then turn the power off to your Air Handler. If your fan stops running, you have turned the power off to your tstat and are ready to start replacing it with your new tstat. I hope you find this helpful. Good Luck!!!
Posted on Feb 07, 2010
The # is on the BACK- yeah go figure, of the unit. Lift the front up from the bottom and it will come off (it goes back on). THEN you will see your number. Mine was a CT3611.
Posted on Apr 07, 2010
Tips for a great answer:
Sep 01, 2011 | Honeywell Air Conditioners
1. Press SYSTEM.
2. Press and hold these two blank buttons until the
display changes. You will have 5 buttons at the bottom of the stat..... Press the two blank button on either side of the middle blank button till the display changes and then scroll down to 0300 and use the up and down arrows to change from 0 to 1 push Done and you should now have Auto.....if you have other ??? look up a Honeywell Pro 8000 stat it will have the same features...
May 05, 2011 | Air Conditioners
Jan 11, 2011 | Honeywell Air Conditioners
Here is a tip that tells you how to get a manual for most any Honeywell product online...
Manual Honeywell How to Find Honeywell Manuals
Jan 04, 2011 | Air Conditioners
Dec 27, 2010 | Air Conditioners
Feb 06, 2010 | Air Conditioners
Aug 28, 2009 | Air Conditioners
Jan 06, 2009 | Air Conditioners
Jul 10, 2008 | Air Conditioners
May 21, 2008 | Honeywell Air Conditioners
100 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: