Question about Amana PTH123B25AJ Heat Pump Air Conditioner
I know this is late but I had to add a solution to this problem since I had the exact same problem and was able to solve it. The probelm is not your control board. On these units, the heat pump compressor will not kick in unless the temperature you set on the control panel is within 2-1/4 degrees (or 4 degrees depending on your unit model. Otherwise, the unit locks out the compressor until the electric heat coil bring the indoor temperature up to that level - and then will switch the compressor back on for heat pump operation. So the problem is not the control panel or the compressor, it the electric heat coil. The coil has two manual limit switches on it that may be tripped and should be checked. The coil can be easily accessed by shutting down the power, removing 4 screws around the air outlet, pushing the screen up and sliding the panel out the top. The power wires can remain in place while the limit switches are reset. Hope it works.
Posted on Nov 06, 2011
I had a problem with the heat not coming on in really cold weather. After much reserch and trial and error I a came to the conclusion that the heating coil was not coming on. The cool will reverse on the first stage, heating coil will come on in the second stage.
Take the front cover off of the unit. Unscrew the screws on the wire mesh and the two screws on the front below them. Pull out the wire mesh and put it aside. Slowly lift the heatng coil assembly striaght up. Grab the area you just took the screws out of. Once you get the coil out you will see the wires are conected to some terminals. On top of one of the terminals it the MANUAL RESET. It does not say it but it has a button on top. Mine was the one on the far left. Push it in till it clicks. Reassemble the unit in reverse. Mine works fine now.
Posted on Mar 09, 2014
You can try to manually reset the heat, however you will likely need to replace the control board altogether. You can purchase it from Amana. They are around $130. You will need to program the new board before it will operate, instructions are included. Take your time and make sure all of the wires are installed correctly or you will have problems.
Posted on Feb 10, 2009
I HAVE COTROL BOARDS TO FIX THAT PROBLEM DREAMGREEN SERVICES 770-233-9987
Posted on Nov 25, 2008
The reset is the size of a pencil tip and is located below the control board on the sheet metal you will see the pin hole,you have to remove the cover to see it
Posted on Nov 17, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jul 20, 2017 | Amana Heating & Cooling
Mar 13, 2017 | Amana Heating & Cooling
Feb 02, 2013 | Amana In Wall Install Kit For Digismart...
Feb 12, 2011 | Amana PTH153B50AM Air Conditioner
Jan 23, 2009 | GE Zoneline AZ38H12DAD Split System Air...
Feb 02, 2016 | Amana PTH123B25AJ Heat Pump Air...
10,647 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: