Question about Ruud UAMB Air Conditioner
3.5 ton Ruud M/N URGG roof package unit.
In the AC mode my unit calls for cooling cycles on the fan starts but the compressor short cycles off then starts a few minutes later.
BAD FAN CONTROL RELAY
Posted on Nov 30, 2008
If the unit is low on freon it will short cycle but a compressor internal overload will cause it to. Lets hope its the freon. Has it been frezzing up lately. Low freon is the cause most of the time. Make sure your filters are clean and both fans are running. Hi head can cause this to. (fans not running) How old is this unit. Maybe the coils need to be cleaned. Sound like this unit may need a check up and a good cleaning.
Posted on Nov 02, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 17, 2013 | Ruud Matching Split Air Conditioner
Jul 02, 2013 | Ruud Heating & Cooling
Jun 01, 2010 | Heating & Cooling
Jan 15, 2010 | Heating & Cooling
Jun 29, 2009 | Heating & Cooling
Oct 29, 2008 | Ruud Heating & Cooling
Sep 20, 2008 | Ruud UAMB Air Conditioner
May 28, 2008 | Ruud Matching Split Air Conditioner
Nov 20, 2007 | Ruud Central System Air Conditioner
Aug 08, 2013 | Ruud UAMB Air Conditioner
373 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: