Question about Goodman Heating & Cooling
I have a heat pump system with a copeland scroll compressor. 1st copeland compresoor ran for 4 year and failed. My second copeland compressor just failed after 3 years. It's in a Goodman CPLT36 condensing unit. I've also lost my defrost timer circuit board and condensing fan.
I really don't use the ac part. Just the heatpump as the unit is installed on the coast.
I have good slope for oil return. System seems to be charged properly.
Any ideas as to why I keep lossing compressors?
I have scroll chiller contains scroll compressor tandom circuit. One of the compressor failure from it due to unbalance of the winding. Previously compressor thermistor opens two to three times. Also one phase open in contactor of the compressor. Can you guide me regarding the reason of compressor failure and what is the next step for the replacement of compressor. Also give guide line for the points take care.
Posted on Mar 27, 2010
Garyfiskse only possible things i can think of is that your unit have dirty coil or improper size of run capacitor
Posted on Oct 14, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 25, 2016 | Heating & Cooling
Jul 05, 2011 | Goodman Heating & Cooling
Feb 18, 2011 | Goodman Heating & Cooling
Jun 18, 2010 | Intertherm P3RA-036K Air Conditioner
Apr 21, 2010 | Heating & Cooling
Aug 03, 2009 | Heating & Cooling
Apr 20, 2009 | Heating & Cooling
Nov 24, 2008 | Weather King 12AJA4801AH Air Conditioner
2,432 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: