Question about Goodman Air Conditioners
I have a heat pump system with a copeland scroll compressor. 1st copeland compresoor ran for 4 year and failed. My second copeland compressor just failed after 3 years. It's in a Goodman CPLT36 condensing unit. I've also lost my defrost timer circuit board and condensing fan.
I really don't use the ac part. Just the heatpump as the unit is installed on the coast.
I have good slope for oil return. System seems to be charged properly.
Any ideas as to why I keep lossing compressors?
I have scroll chiller contains scroll compressor tandom circuit. One of the compressor failure from it due to unbalance of the winding. Previously compressor thermistor opens two to three times. Also one phase open in contactor of the compressor. Can you guide me regarding the reason of compressor failure and what is the next step for the replacement of compressor. Also give guide line for the points take care.
Posted on Mar 27, 2010
Garyfiskse only possible things i can think of is that your unit have dirty coil or improper size of run capacitor
Posted on Oct 14, 2011
Tips for a great answer:
Jul 25, 2016 | Air Conditioners
Jul 05, 2011 | Goodman Air Conditioners
Feb 18, 2011 | Goodman Air Conditioners
Jun 18, 2010 | Intertherm P3RA-036K Air Conditioner
Apr 21, 2010 | Air Conditioners
Aug 03, 2009 | Air Conditioners
Apr 20, 2009 | Air Conditioners
Aug 02, 2008 | Goodman CLQ36AR49 Air Conditioner
2,430 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: