Question about Water Heaters
All new parts in beckett oil burner. after z guaged the igniter and gun nozzel the tube is collecting oil? tried resetting nozzel distance to cone, but no difference. burner oil pump filter and screen changed, complete boiler vacumed out, also. sure can use some help? thanks, very much.
Problem is pump-must replace- there is a valve inside unit that holds pressure to about 150psi -it is leaking by when unit shuts down- causing problem. If left unrepaired you could blow chimeny connection with bad ignition. good luck
Posted on Nov 02, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 01, 2016 | Water Water Heaters
Oct 06, 2014 | Water Heaters
Apr 11, 2011 | Rheem Water Heaters
Sep 20, 2010 | RTO Bock Water Heaters 51E 50 gal 152,000...
Apr 22, 2010 | General Electric GE SmartWater Household...
Apr 09, 2010 | Rheem 40 GAL ELEC TALL Water Heater 6YR SC...
Feb 13, 2010 | Reliance & 50gal Electric Water Heater
Jul 09, 2009 | Northern Tool Water Heaters
Feb 01, 2009 | Water Heaters
Jan 16, 2018 | Water Heaters
770 people viewed this question
Usually answered in minutes!