Question about Honeywell Electronic Programmable Heat/Cool Thermostat - CT3300A100 Heater
Our Honeywell rth230B is not turning the furnace on in that zone of the house. The other thermostats in other heat zones are fine but this one will not bring the hot water baseboard heating to that room. We were mighty cold sleeping last night. The display seems ok.
What we tried:
Resetting the filter button.
Using manual mode and the desired temp.
Switching from heat to off to cool and back.
Prior to the no heat problem, radiator in that room had been "gurlgly". We went away for four days and turned the heat OFF then. When we returned, we could not get the heat back on. The pipes could not have frozen b/c it was not below 32 while we were away.
Help us please--
It is not your thermostat, it is an airbound zone. The gurgly noise you heard was that water and air flowing through the radiator. The zone needs to be purged either at the boiler, or through vents on the radiator. Hope this helps
Posted on Jul 20, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 29, 2013 | Heating & Cooling
Jan 01, 2011 | Honeywell Programmable Thermostat Heater
Feb 02, 2010 | Honeywell Programmable Thermostat Heater
Oct 16, 2009 | Honeywell Electronic Programmable...
Oct 08, 2009 | Honeywell Electronic Programmable...
Oct 01, 2009 | Honeywell Programmable Thermostat Heater
May 18, 2009 | Honeywell Focus 6300B 5-2 Days...
Nov 12, 2008 | Honeywell Programmable Thermostat Heater
Mar 07, 2008 | Honeywell Programmable Thermostat Heater
292 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: