Question about Goodman CLQ36AR49 Air Conditioner
New Goodman H. Pump 2.5 ton 13 SEER unit seems to blow a lot of cold air berore warming up. I talked to installer about putting the fan on low speed but he is reluctant to do that. Any suggestons
Heat pumps generate heat from compressing freon and take a while to generate enough heat to be useful. never expect robust heat from a pump like an oil burner or a gas furnace, but they do heat great and are cheaper to operate. do this . if you are still using an old mercury bulb stat change it to a digital one. this will hold an exact temperature and time off between cycles will be less and the indoor coil will stay warm between short cycles, with an old mercurry stat you set it at 70 and it may run up to 73 and stay off till 68. thats a long off cycle and when call resumes the coil has gotten cold and has to start all over again. also dont wait till it gets cold to run a heat pump. turning it on and off as it gets cold is not correct. you should select a temp ,usually 71 for heat and set it and leave it on to do its thing.you may want to check the charge. hot gas discharge is usually 100 degreees hotter than outdoor temps after 15 minutes run time. for example if its 40 outside the big freon line outside thats insulated should be about 140 degrees. or you can run it 15 minutes and grab it with your hand . it should be almost uncomfortable to hold any length of time. careful some get quite hot. you also have the option of hooking up the electric strip to automatically come on if you push the stat up 2 degrees hotter than the temp in the room. that way you get heat pump and strips till temp gets within 2 degrees of set point and the strips shut off and pump maintains.good luck
Posted on Nov 02, 2008
Insulate the ductwork better
Posted on Sep 13, 2012
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 01, 2015 | Goodman Manufacturing Goodman GPH1348M41 4...
Sep 14, 2014 | Goodman GSH130301 Heat Pump, 3 Ton, 13...
Feb 05, 2014 | Goodman Manufacturing Goodman GPH1348H41...
Oct 25, 2013 | Goodman Manufacturing...
Apr 02, 2013 | Goodman Manufacturing GPH1336H21A -...
Jul 13, 2010 | Goodman CLQ36AR49 Air Conditioner
Jul 12, 2010 | Goodman CKL36AR36 Air Conditioner
May 06, 2009 | Goodman Heating & Cooling
Jul 02, 2008 | Amana PTH123B25AJ Heat Pump Air...
191 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: