Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
4-wire typical wiring of a thermostat is: Y (Yellow) G (Green) W (white) and R (red). Inspect the thermostat to see if it has a jumper from R1 to R2. If not, put your red wire on R2. On a 5-wire thermostat you may have a blue wire. This will go to the common terminal (usually C but sometimes B) check the inline fuse in the air handler to see if it has blown. Replace it only after wiring the thermostat correctly.
Posted on Dec 03, 2007
Since you have three on/off timing modes could there be an overlap in the times?
The wires in the unit might be crossed. (don't always assume the contractor who wired maintained the correct colors , I have a friend who blew out a heating pipe because when a replacement motor valve was installed it was never wired right and the plumber assumed the colors were correct so no overtemp shutoff created steam in PVC pipes, OPPS)
There fore maybe one is still coming on. Do you have more than one heating zone? IF so see below
I guess the main question is why manually turn it off? why not use the program.
I will assume your heat is know as forced hot water heating. My house is multizoned however when the zone calling for heat turns off (zone valve closes) I installed a bypass valve in the lowest zone in the house, and reduced the circulator low shut off temp to 130 F which means even though the heat isn't on my circulator will continue to run dumping this excess heat in the lowest part of house to rise through house. (the spring loaded water valve allows the heated water to flow into this zone )We do have two thermistats. And even though the lowest one is not calling for heat the radiators are hot when the excess is dumped into this zone. So investigate and see if your system might be similar. (multizone).
Investigate your wiring, reprogram, replace any battery backup.
Posted on Dec 19, 2007
SOURCE: Door Hinge Replacement
remove spring that holds the rubber bellows to front of machine
peel back and fish out plate from inside cavity of machine
then refit plare and reverse process
Posted on Mar 15, 2008
yep the wires will hook up to the same designations, just write down what color was connected where. You will need to set the thermostat up for your particular situation...gas, electric, heat pump, ect. The installation maunel is very clear on this aspect so you should not have a problem.
Posted on Nov 14, 2008
Tips for a great answer:
Oct 21, 2017 | Heating & Cooling
May 11, 2011 | Honeywell Programmable Thermostat Heater
Feb 23, 2011 | Honeywell Programmable Thermostat Heater
Jan 18, 2010 | Honeywell Programmable Thermostat Heater
Nov 05, 2009 | Honeywell Programmable Thermostat Heater
May 08, 2009 | Honeywell Programmable Thermostat Heater
Oct 30, 2008 | Honeywell Programmable Thermostat Heater
331 people viewed this question
Usually answered in minutes!