Question about Carrier 38BRC048 Air Conditioner
I have in my home a central Air/heater Carrier Model 58RAV095-13116 Series 130. Througout the whole summer, I have been using the aircon and it runs fine. Yesterday I turned on the heater. I noticed that the motor/blower will start and after few seconds the wire inside would glow(this unit is pilotless and does not use matches). I would expect gas to lit afterwards but it won't. The wire glow would simply die down. What must be wrong? I need help.
Either the gas at the outside valve is off, or the gas valve at the furnace may be off, or the switch on top of the gas valve in the furace may be off. if they are all on, then you may not be getting a call for heat from the stat to the furnace control board. check to see if you are getting a 24 volt signal from the stat to the w terminal and common terminal on the furnace board. if you are then check to see if the voltage is arriving as 24 volts to the wires at the gas valve itself . if it is then the gas valve is possibly bad. if it is not then the board is possibly bad.look for loose or broken connections on the low voltage wiring. most unusual that the board does everything else but send power to the gas valve. you need to zero in on the valve i think and start by turning off power and that should restart the sequence of operation and you can observe it step by step . if you are not getting a call for heat then the stat may be bad be sure you are in heat , fan in auto and temp pushed up to max. if no 24 volts is sent to furnace board white and common low voltage board then stat is bad. remove it if you think its faulty and jumper the white and red wires together on the subbase. that duplicates what the stat normally does. if the furnace lights its the stat. having said that i realize the stat has to be sending a heat signal or the other stuff would'nt start. so..... back to the furnace board. check that 24 volts in from stat and 24 out to valve and that will put you on your problem item. good luck
Posted on Oct 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 07, 2015 | Dayton Heating & Cooling
Feb 12, 2012 | Heating & Cooling
Jun 01, 2011 | Carrier Heating & Cooling
Apr 05, 2011 | Heating & Cooling
Feb 21, 2011 | Carrier Heating & Cooling
Oct 07, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 03, 2009 | Heating & Cooling
Sep 01, 2008 | Carrier Heating & Cooling
May 28, 2014 | Carrier 38BRC048 Air Conditioner
384 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: