Question about Heating & Cooling
In a hydronic system for heating you must insure that the pressure on the boiler is maintained during the process of bleeding off the air from the system. There is a regulator for the water make-up to the system which normally maintains 12 PSI with the boiler cold. If this is stuck or fails to open you will loose the pressure on the system when bleeding the air off. Most are adjustable. Loosen lock nut on the adjustment stem and turn the screw (clockwise) to increase the pressure. Count the turns as you adjust it and return it to the original setting when you finsh bleeding off the air.
Posted on Oct 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 09, 2016 | Heating & Cooling
Jan 26, 2016 | 2004 Dodge Dakota
Oct 04, 2014 | Home
Feb 22, 2011 | 1999 Buick Century
Aug 27, 2010 | 1979 Chevrolet C/K 3500
Nov 14, 2009 | Plumbing
Oct 23, 2009 | DeLonghi EN680.M
Oct 10, 2009 | Water Heaters
May 15, 2009 | 2005 Honda Pilot
84 people viewed this question
Usually answered in minutes!