Question about Hunter Vaulted Ceiling Mount - Antique Brass Fan
I am installing a ceiling fan and light kit and am having trouble wiring them. The wall has 2 switches, but only one romex goes to the fan. There are two blacks and two whites coming into the box. One white coming in is connected to the bottom switch and the other white is connected to the white going out. One black wire coming in is connected directly to the top switch on one side. The other black wire coming in is wired to the one going out and a third is connected to this and runs to the other side of the top switch. I have on the ceiling one black and one white. How do we wire this ceiling fan and light kit to this configuration where one switch is for the light and one for the fan. The old fan was wired for these switches but unfortunately our son took it down without us seeing how it was wired first.
If you have only one black and one white in the ceiling to connect the fan / light to , then you have only one switch for this ceiling box. The fan / light will connect the white wires together and then the two colored wires on the fan to the black ceiling wire. In order to use separate switches for the fan and the lighht a 4 wire cable must go from the switches to the light so you have a red and black wire to switch the two separately .
Posted on May 04, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 23, 2016 | Dryers
Jul 07, 2011 | Heritage (5BFW52NK4KG) 52'' Ceiling Fan
May 01, 2011 | Hunter Ceiling Fan Light Switch Control
Apr 16, 2011 | Solar 2-wire Pull Chain Light Switch For...
Feb 01, 2011 | Broan-NuTone FAN CONTROL SWITCH
Apr 25, 2009 | Minka -Aire Brushed Nickel Remote Control...
Jan 21, 2009 | Solar 2-wire Pull Chain Light Switch For...
May 30, 2008 | Hampton Bay 52 In. White Redington...
Aug 10, 2007 | Hampton Bay 52 In. White Redington...
Jun 24, 2017 | Broan-NuTone Dryers
494 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: