Question about Heating & Cooling
SOURCE: Baxi Combi 80e
i need to know boiler specifics- make and model but sounds like either the air pressure switch seized or the main printed circuit board, if the boiler has an overheat thermostat please ensure that the little red button hasnt popped out because this will prvent the boiler firing up- refer to the manufacturers instructions for location of the o/heat stat
Posted on Sep 18, 2008
The first thing you need to do is to put some more water into your heating system. This is usually done by allowing water from your (pressurised) domestic cold water supply to flow into the system: On older boilers, this is done with a connection (often made with a removable hose) on the pipework just outside the boiler. Newer boilers may have a built-in connection with some sort of removable link (sometimes looks like a plastic key).
Once you've got the boiler up to working pressure (typically about 1 bar - 15 psi), you should be able to bleed your upstairs radiator properly.
This may be all it takes, though the pressure excursions you're getting when you run the hot tap suggest there may be another problem. See what happens to the pressure as the boiler heats up and cools down. There really ought to be very little pressure difference between the two conditions. If you see significant changes, this usually means that the "pressure vessel" (or in hydraulic terms, system accumulaor) has lost its air charge.
The pressure vessel is a metal container inside the boiler, usually painted in red enamel. Somewhere near the top, you will find a schrader valve (like the one on a car tyre), and you can use this along with a tyre pump to replenish the air in the top of the vessel. This will reduce your pressure transients for a while, but you need to keep an eye on it. If the problem returns, you probably need to replace the pressure vessel (or clag another one into the plumbing alongside the boiler).
Posted on Feb 03, 2009
does the boiler come on when the hot water tap is run if not change the hot water flow switch or the diaphram in the hot water flow valve it may be split
Posted on Aug 17, 2009
Tips for a great answer:
Nov 06, 2012 | Heating & Cooling
Oct 27, 2012 | Universal 900MM Super Thermocouple Baxi...
Jan 23, 2011 | Water Heaters
Oct 12, 2009 | Water Heaters
Feb 19, 2009 | Combi Centre DX - Mango
Feb 03, 2009 | ACCO Brands Water Heaters
Oct 29, 2008 | Heating & Cooling
Aug 05, 2008 | Heating & Cooling
May 05, 2008 | Combi Centre DX - Mango
260 people viewed this question
Usually answered in minutes!