Question about Air Conditioners
Be sure the fan setting on the stat is set for auto, not on. in this mode the fan should only run when there is a call for cool or heat.if the fan continues to run check at the control board to see if you are getting 24 volts low voltage between green and common. if you are then the stat is bad. if youaren't then your electric control board is possibly bad. a lot of gas furnaces fall into a failsafe mode when a sensor or function fails and the blowers stay on 24 7. you may well have several problems from what you are saying. if you turn everthing off and start a new cycle for heat the first thing that should fire up is the induced draft motor , then the ignotor, then the gas valve. you can check each item with a meter , generally 120 volts to the induced draft motor, then 120 volts to the ignitior, the 24 volts to the gas valve. then ignition and 120 volts to the motor. most furnaces have a heat terminal and a cool terminal on the board. common to heat should get 120 volts on a call for heat after the sequence of operationb has taken place. 120 volts should be sent to cool terminal on a call for cool. a continueous blower is a sign of a failed safety. perhaps the motor failed and the safety opened and the motor was replaced but the safety never reset?. look at all the little micro temp sensors around the burner. they are like little breakers and need to be pushed in to reset . usually like a little stem that pops out from a metal or plastic dic. some are size of a quarter, some the size of a dime.
Posted on Oct 29, 2008
Tips for a great answer:
Feb 24, 2015 | Filter Air Conditioners
Oct 13, 2014 | Air Conditioners
Jul 22, 2013 | American Standard WCZ036F Air Conditioner
Feb 05, 2011 | Air Conditioners
Feb 15, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 19, 2009 | Air Conditioners
Nov 04, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Feb 02, 2009 | Air Conditioners
Oct 02, 2008 | Air Conditioners
Sep 05, 2008 | Air Conditioners
120 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: