Question about Honeywell Heating & Cooling
If the room is at the set temperature even when the rad are warm the boiler is doing its job. It takes steel rads up to an hour to cool down so if they stay warm to the touch that is normal.It takes steel rads a long time to heat up when they get cold so its cheaper to let them not get real cold.I was told not to put a programmable thermostat on our boiler simply because it takes a lot of gas to bring your house up even two degrees. I run a non programmable and set our heat at 72 degrees and do not touch it all winter. There should be a water shut off on each rad so if you want your bedroom cooler just shut that shut off on that rad off.
Posted on Apr 10, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I would really call your installers back mate.
If you have anything to measure air temp with I will take you though some tests.
But at this point I would say that your air con does not have any gas and the installers should come back. If they will not come back you should contact Hitachi warranty
Hope this helps
Posted on Jan 11, 2009
SOURCE: My outdoor heat will not
you need to go oside and look for a red reset button on the unit. you tripped the high ressure switch when you let your filter get that dirty. go check on this and when your done if it still is not working then ask me more.
Posted on Jan 25, 2009
SOURCE: GE Heat/Cool model AJHS10DCBM1
OK I will be looking over the manual. Now that squeal sounds like the squirrel cage fan scraping the housing around it. Those units are so tight fit they can be twisted one way or tightened a little to much they scrape. I love them for there silence win they work right but hate them because my hand are too big to move things around inside them. Stay in touch I will be looking around while
multi-tasking today- I'll be here!
Posted on Feb 02, 2009
SOURCE: Heat pump cycling on and off.
It sounds as if you you have a low charge of refrigerant, r22. When the unit comes on outside, the outdoor coils become the lowside, there is a low pressure switch that is tripping out contactor protecting the compressor.
Posted on Mar 11, 2009
Tips for a great answer:
Jun 23, 2014 | Heating & Cooling
Dec 13, 2012 | Water Heaters
Mar 05, 2017 | Water Heaters
Feb 01, 2010 | Desa International CBN30T Central Heating...
Apr 26, 2017 | Honeywell Programmable Thermostat Heater
Mar 25, 2009 | Water Heaters
Feb 18, 2009 | Honeywell Programmable Thermostat Heater
Jan 05, 2009 | Water Heaters
Aug 07, 2008 | Heating & Cooling
Mar 15, 2008 | Computers & Internet
53 people viewed this question
Usually answered in minutes!