Question about Heating & Cooling
Fires up for HW but not for CH
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If the valve runs at other times, the valve is OK. you have a relay somewhere that is not sending signal to the valve when in that mode.
Trace down all the relays for that cycle and check voltage going int, coming out, and to see if the coil is enrgised.
Posted on Jan 01, 2009
may just be a defective display PCB, byt more often than not, its the more expensive main primary PCB. Ideal actualy modified this PCB, and has a pre-fix of VF on it, and is orange in colour
Posted on Mar 03, 2009
SOURCE: combi boiler no DHW
if the boiler fires when the tap is opened then the diverter valve is working ok it must be a blocked plate heat exchanger which is the stainless steel rectangular block inside the boiler connected to the pump and the mains cold water.
it will be blocked on the central heating part probably with black scale. it is possible to clean out but sometimes it is better to just change the plate. but remember to flush the system as well or the same thing will happen.
Posted on Mar 30, 2009
Tips for a great answer:
Feb 25, 2017 | Water Heaters
May 19, 2014 | Water Heaters
Dec 20, 2012 | Water Heaters
Sep 11, 2011 | Heating & Cooling
Mar 27, 2011 | Honeywell Heating & Cooling
Oct 07, 2009 | Comfort-Aire RAD-243 Air Conditioner
Jan 01, 2009 | Heating & Cooling
17 people viewed this question
Usually answered in minutes!