Question about Intertherm P3RA-036K Air Conditioner
Need to know if its a heat pump or electric strip heat. if its a heat pump then compressor and outdoor fan will run on call for heat. being an intertherm and most of them are electric strips, i'll guess. the call for heat sends 24 volts to the heat sequencer. lots of wires connected to what is called a stack switch. wires closest to the mounting plate are 24 volts and when energized they heat up a bimetal disc that clicks on in 90 to 160 second s and energizes the first strip and fan and a few seconds later the 2nd and 3rd strips kick in. for every strip operating you pull about 20 amps. if fan is working then the other parts of the sequencer are failing to close and put power to the strips or the strips themselves are bad. these are very very confusing and tricky to work with. i have to work on them hot to observe where the problem lies. very dangerous as you are going to have to trip a 90 amp breaker if you make a mistake , not to mention the parts are not available except through wholesale only supply house. i feel pretty confident the sequencer is going to be bad and i think its probably best you call a pro to get this one squared away. sometimes when you are tinkering with old sequencers they literally crumble apart in front of you, they can get that brittle. it can be quite an adventure and not for the faint of heart when its hot. good luck.
Posted on Oct 28, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 18, 2014 | Ruud Rheem Squirrel Cage Blower Wheel...
Jun 01, 2017 | Heating & Cooling
Sep 05, 2012 | Amana PTH123B25AJ Heat Pump Air...
Jan 13, 2011 | Heating & Cooling
Feb 22, 2010 | 1994 Chevrolet C1500
Jul 30, 2009 | Heating & Cooling
Jul 07, 2009 | Heating & Cooling
Jun 27, 2009 | 2001 Pontiac Grand Prix
May 05, 2009 | Mastercool 67680 Evaporative Cooler Air...
196 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: