Question about Honeywell Heating & Cooling
Jumper red to white and it should bring on a call for heat. if it does then you probably damaged stat on reattachment. do you self a big favor and go to a digital stat. you probably have a red white yellow and green wire. hook them up same way on new stat. if you have an extra wire you can pull a common and power the new stat off the transformer, if not you can get one that uses batteries. robertshaw makes some good ones 9400 9401 etc. you need straight cool with gas furnace. they are great. no need to get to fancy and avoid the ones with programming and all. they are way to complicated unless your into lots of programming and tech details. plus those old honeywells are almost impossible to get perfectly level on the wall and if they are not level they will perform way out of whack
Posted on Oct 28, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 19, 2014 | Honeywell Ct87k Round Heat Only Manual...
Jan 11, 2011 | Honeywell Heating & Cooling
Dec 16, 2010 | Honeywell Programmable Thermostat Heater
Nov 16, 2010 | Honeywell Heating & Cooling
Aug 13, 2010 | Honeywell CT500 Digital Heat / Cool Manual...
Jan 04, 2010 | Honeywell CT87B ROUND HEATING&COOLING...
Dec 18, 2009 | Honeywell CT87B ROUND HEATING&COOLING...
Dec 31, 2008 | Honeywell Programmable Thermostat Heater
Feb 09, 2008 | Honeywell CT87B ROUND HEATING&COOLING...
68 people viewed this question
Usually answered in minutes!