Question about Heating & Cooling
My 5 year old Sears gas furnace has a hum coming from the front panel of the blower compartment when the blower is not on. Is this normal.
A very subtle hum or buzz is normal and is the transformer that creates 24 volt control voltage continually. some are noisier than others . sometimes a tap or bending of the transformer will tweak the metal enough to make it quieter. they can also get loud if incoming voltage is not correct. incoming 120 volts on a furnace is not usually a problem but the transformers are usually wired to the available incoming 230 voltage or 208 voltage if it is a heat pump or electric heat. If it is powered by 230 or 208 volts as most heat pumps are ,then you need to verify which you have and connect the appropriate leads from the trans former to power . it tells you on the side of the transformer which to connect to 230 and which to connect to 208. tape or cap off any unused leads.since you have not mentioned any performance problems i assume the fan does come on when called for and that it is not the loud hum you hear. switching the fan switch at stat to on should bring the fan on right away. if it doesn't then you may hear a loud hum and then youll need to check the fan motor and capacitor. but it sounds like a noisey transformer from here.
Posted on Oct 28, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 10, 2016 | Goodman Heating & Cooling
Oct 20, 2013 | Ruud Heating & Cooling
Oct 08, 2012 | Heating & Cooling
Dec 07, 2010 | Heating & Cooling
Oct 27, 2010 | Amana Heating & Cooling
Oct 22, 2010 | Heating & Cooling
Jan 06, 2009 | Heating & Cooling
Dec 07, 2008 | Carrier 38CKC036 Air Conditioner
390 people viewed this question
Usually answered in minutes!